Provide power to 24 Vac circuits in heating/cooling control systems. Intended for use in systems with predictable, uniform loads. Can be used in any application that does not exceed the listed ratings.
Rated at 50 VA.
Color-coded leadwires for primary connections and screw terminals for secondary connections, fixed 1/4 inch (6 mm) male quick-connects or color-coded leadwires for both primary and secondary, are standard.
Meet NEC Class 2 requirements. Meet Underwriters Laboratories Inc. Standard UL 1585 and are identified. Class 2 not wet, Class 3 wet.
Electrical Ratings -Primary Voltage 120 Vac, 208 Vac, 240 Vac.
Electrical Ratings -Secondary Voltage 27.5 V.O.C..
Frequency 60 Hz.
Mounting Foot mounted, plate mounted on 2x4 in. or 4x4 in. outlet box, clamp mounted using outlet box knockout, or panel mounted.
Electrical Connections (Primary)(in.) 9 in. leadwires.
Electrical Connections (Primary)(mm) 229 mm leadwires.
Electrical Connections (Secondary)(in.) (2) screw terminals.
Electrical Connections (Secondary)(mm) (2) screw terminals.
Electrical Ratings -Output 24 Vac at 50 VA.
Dimensions (in.) 1 11/16 in. high x 3 3/16 in. wide x 1 3/4 in. deep .
Dimensions (mm) 43 mm high x 81 mm wide x 75 mm deep.
Temperature Ratings (F) -20 F to +105 F.
Temperature Ratings (C) -29 C to +41 C.
Approvals, Underwriters Laboratories Inc UL Listed: A,C,F models. File # E14881.
Approvals, Canadian Standards Association CSA Certified: A & B models.